All Aluminium Conductor (AAC) have high ratio of electrical conductivity to weight, high flexibility, high Current Carrying Capacity and low UTS. Also, the aluminium has low levels of brittleness
All Aluminium Conductors (AAC) are used in low voltage overhead lines in urban areas and in high voltage substation conducting. They are also used in very cold areas due to low brittleness of aluminium in the MV lines.
|01||Conductor Area||10.6mm2 to 1095mm2||0.0164 in2 to 1.6973 in2|
|02||Conductor construction||7Al Alloy to 91 Al Alloy|
|03||Conductivity of Al Alloy||61 % to 61.2 %|
|SR. NO.||CONDUCTOR CONSTRUCTION||MODOLUS OF ELASTICITY*||LINEAR COEFFCIENT*|
|01||7 Strands||60000||8702||23.0 X 10-6||12.8 X 10-6|
|02||19 Strands||57000||8267||23.0 X 10-6||12.8 X 10-6|
|03||37 Strands||57000||8267||23.0 X 10-6||12.8 X 10-6|
|04||61 Strands||55000||7977||23.0 X 10-6||12.8 X 10-6|
|01||Permissible Temp in continuous operation||75°C||167°F|
|02||Temp in a short circuit (duration up to 5 s)||200°C||392°F|
Note: The Catalogue conductor Parameter are informative and can be customized as per Project Requirements.